The failure rate and life of electric/control and broadcast devices are strongly affected by heat around.
Current thermal issues and solutions with SPACECOOL
Internal electric/electronic devices deteriorate/fail
Device life ⬆
Maintenance cost ⬇
Measurement errors occur
Trust in measurements lost
Less measurement error
Cooling requires energy consumption and CO2 emissions
Cooling cost ⬇
CO2 emissions ⬇
Common outdoor unit insulation/heat release/cooling device issues
●When a heating element is present, heat builds up
●Once heat builds up, it’s hard for internal temperature to drop
●For air intake Sucks in dust, humidity
●Regular maintenance is necessary
Introduction example and effect of high voltage receiving and transforming switchboard
Air conditioning power consumption is reduced by approximately 21% on sunny days and by approximately 20% over the entire period, including rainy and cloudy days.
Test date： Measured the power consumption reduction effect over the entire period from July 22nd to August 31st before construction and from September 1st after construction.
Installation location：SPACECOOL is installed on the roof, east, west, south, and north walls.
Internal storage equipment：Vacuum circuit breaker 3.6kV 600A x 6 units
Molded transformer 3Φ3.3kV/210V 100kVA x 1 unit
Molded transformer 1Φ3.3kV/210-105V 100kVA x 1 unit
DC power supply 2.6kVA x 1, storage battery MSE 50Ah @ 10 hour rate 54 cells (MSE-50-12 x 9, DC108V/set)
Air conditioner capacity 1Φ100V 615W×3
As a result of monitoring air conditioning power consumption with and without this material, it was confirmed that air conditioning power consumption was reduced by approximately 21% on sunny days and by approximately 20% over the entire period, including rainy and cloudy days.
Examples of introducing electronic control panels and their effects
Reduces the temperature inside the electronic control panel by approximately -10°C
Internal heat source：Device modeled after an inverter (200W)
No heating element：Roughly 10℃ cooler than regular paint, Confirmed to be 5℃ cooler than douser.
Heating element present：Roughly 10℃ cooler than ordinary paint, Roughly 8℃ cooler than douser.